The sign must be charged for a minimum of 60 minutes to become fully operational.
illumination source must be supplied by a circuit not controlled by an automatic timer or sensor and whose controls are accessible
only to authorized personnel.
3. External illumination source is to be energized at all times during building occupancy.
Lighting levels on the sign face(s) should be confirmed after any change in external lighting.
5. It is recommended
that inspections be performed in accordance with applicable codes.
6. Install sign indoors only, where not exposed
to direct sunlight, moisture or temperatures outside the range of +10 degree to 40 C (50-104 F).
This exit sign can be used as a primary or secondary exit
sign in accordance with the UL924 standard for "Emergency Lighting and Power Equipment", Eighth Edition, July 2001
revisions. Install in compliance with NFPA Life Safety Code 101 or other applicaple buiding or fire codes for photoluminescent
exit signs. They are non-explosive, non-corrosive,non-toxic, non-radioactive and non-electric, requiring no electrical wiring